PRIER C-244 provides a year round source of water to areas of structures that are subject to freezing temperatures. The hydrant valve is connected to the supply piping in the heated portion of the structure, eliminating the possibility of freezing. Ordering the C-244 gives you the same style hydrant as the C-144 but with a vandalproof extended lock shield with operating key.
The PRIER C-244 has all the characteristics of the historically proven C-234 with the added protection of an anti-Siphon vacuum breaker and backflow check valve. It is available in stock lengths from 1 1/2" to 24", longer sizes are available on request.
PRIER has been manufacturing the C-144/244 Freezeless Hydrants since 1990. This freezeless hydrant has truly passed the test of time. It is a simple operating product that is fairly simple to repair.
Possible Repair Issues for the C-244 Freezeless Wall Hydrant:
1. When the water is running, water leaks out from behind the handle [VIDEO]
This is a common maintenance occurrence for any packed valve of any brand or manufacture. It is overcome by simply tightening the packing nut with a crescent wrench. This will force the packing tighter around the stem to eliminate leakage.
Occasionally, the packing will need to be replaced if the packing nut has been repeatedly tightened.
The part required for this is a C-134KT-803 Packing Kit
A freezeless wall hydrant shuts off inside the heated portion of the structure therefore, the water inside the hydrant will drain out after shutoff. The shutoff point could be any distance from 4" to 24" inside the structure. This installation should also be pitched to allow the water to easily drain out of the hydrant. The hydrant may drip for up to 60 seconds after shutoff. If the water continues to drip after that time, you most likely need to replace the bibb washer.
PRIER uses a OO Beveled Bibb Washer for the C-244 freezeless wall hydrant, part number C-134KT-802. The bibb washer is a standard "OO" Beveled Bibb Washer, also available at your local plumbing wholesaler.
3. Water leaks from under the plastic cap on top of the valve [VIDEO]
The vacuum breaker has begun to leak. This problem often occurs when the hose is left on the valve and the plastic cap is ruptured by freezing, or the rubber seating surface needs to be replaced.
The replacement kit for this repair is part number C-144KT-806.
C-144KT-806 Vacuum Breaker Replacement Kit
*PLEASE NOTE: Since the creation of this video, we have updated our vacuum breakers to aluminum caps as shown above. The C-144KT-806 and 630-7500 are now universal vacuum breaker kits and will fit all past and present PRIER and Mansfield style residential hydrants.
4. Water is leaking from the hydrant inside my house.
Unfortunately, your freezeless hydrant is broken, most likely beyond repair. This happens when the water becomes trapped within the hydrant. The water freezes, expands and ruptures the copper shaft of the hydrant located on the inside the structure. The most common reason for this problem is leaving the garden hose attached during freezing weather, or the hydrant was not installed with the proper drainage pitch.
DO NOT OPERATE THE HYDRANT IF THIS HAS OCCURRED.
Please remove the handle to prevent accidental operation until the problem is repaired by your plumber.
For any one of numerous reasons, your operating key may be missing. PRIER's operating key is unique to its products - it has one flat side and the rest is rounded. This style key mates perfectly with our stem-end for a snug fit and years of reliable operation.